Method of operation
Ultrasonic humidifier function principle
Ultrasonic humidifiers operate according to the principle of "ultrasonic atomization".
A 48 V alternating voltage is rectified on an atomizer PCB and converted into a high-frequency signal of 1.65 MHz. This signal is transferred to an oscillator installed in the water bath, which converts it into a high-frequency mechanical oscillation. The integrated oscillators are referred to as thickness oscillators, which change their thickness 1.65 million times a second in line with the applied signal of 1.65 MHz.
Login on E-Stulz
for detailed technical specs